The determination of resistance to rapid crack propagation is also known as the Small-Scale Steady-State Test (S4 Test). The ISO 13477 test method typically demonstrates critical performance criteria for PE pressure pipes at below zero temperatures.
The RCP / S4-test is part of Elements global Plastic Pipes & Fittings Testing program, provided to resin manufacturers, pipe extruders, certification bodies and utility companies worldwide, where independent, reliable and reproducible test data is required for product classification and life time evaluation.
ISO 13477, S4-TEST
ISO 13477 specifies a test method also known as the Small-scale steady-state test (S4 test) for determination of arrest or propagation of a crack initiated in a thermoplastic pipe at a specified temperature and internal pressure. The aim is to assess the performance of thermoplastics pipes that are intended for the supply of gases or liquids. In the latter case air may also be present in the pipe. This test typically demonstrates critical performance criteria at below zero temperatures for PE pressure pipes.
A section of a thermoplastic test pipe of a specific length, maintained at a specified test temperature, containing a fluid at a specified test pressure, is subjected to an impact, near one end, in order to initiate a fast running longitudinal crack. The crack initiation process itself is designed to disturb the test pipe as little as possible.
The test temperature and test pressure are defined in the appropriate standards. The fluid is either identical to the one used in the intended application or an equivalent substitute. Rapid decompression ahead of the propagating crack is retarded by internal baffles and by an external cage which restricts flaring of the test pipe at the edges of the fracture.
Hence this technique achieves steady-state rapid crack propagation (RCP) in a short pipe specimen at a lower pressure than in a full-scale test. The tested pipe is examined to determine whether arrest or propagation of the crack has occurred. From a series of tests at different pressures and at constant temperature, the critical pressure or the critical hoop stress for RCP can be determined. Similarly the critical temperature for RCP can be determined by testing at different temperatures at constant pressure or hoop stress.
For more information about our plastic pipe and pipe fittings testing, or to request a quote, contact us today.
We're here to help. Engage with an expert today.
Our plastic pipes testing facility in Sweden is one of only a handful across the globe with a capacity of 5,000 test stations. We provide independent, reliable and reproducible test data for product classification and life time evaluation. Contact our team to discuss your test projects.
Plastic Pipes Testing Services
Hydrostatic Pressure Testing
Determination of long-term hydrostatic strength for plastic pipes to ISO 9080 (MRS) and ASTM D2837 (HDB).
Chlorine Resistance Testing
Evaluation of oxidative resistance to chlorinated water for PE, PEX, PE-RT, and PP materials to ASTM F2023, ASTM F2263, and ASTM F3497-21.
Rapid Crack Propagation, S4 Test
Determination of resistance to rapid crack propagation to ISO 13477 for PE pressure pipes at below zero temperature.
Slow Crack Growth Test to ISO 13477
Determination of slow crack growth to ISO 13477 on pre-notched PE and PEX pipes
High Flow Circulation Loop Testing
Experimental simulation of pipe life expectancy is affected by bend radius, types of fittings and pipe insulation using flowing water.
Plastic Pipes & Fittings Testing
Our plastic pipe testing program offers test data for product classification and lifetime evaluation to resin manufacturers, pipe extruders and certification bodies worldwide.